€ 84.0 0Bids, Location : Miami, Florida, Ship To : US
Honeywell S8600, S8610, S8620 Universal Intermittent Pilot Ignition Module
Honeywell Ignition Control BoardUniversal Intermittent Pilot Ignition ModuleModel S8610U3009/U OVERVIEWUniversal intermittent pilot ignition module replaces multiple field installed intermittent pilot modules supplied by Honeywell, Robertshaw, Johnson, and UTEC (HSC). Uses existing intermittent pilot burner. Includes cross reference, instructions, and accessories for easy replacement. FEATURES· Replaces over 400 White-Rogers, Robertshaw and Honeywell intermittent pilot ignition modules· Provides ignition sequencing, flame monitoring and safety shutoff for intermittent pilot warm air furnaces and heating appliances· Provides 100 percent pilot gas shutoff if pilot fails to light; after 6-minute delay, trial for ignition is repeated. Ignition trial/delay sequence is repeated until the appliance lights or call for heat is removed.· For use with Natural or LP gas· For use in single rod or dual rod/remote sense applications· Includes spark cable adapters to allow field replacement of both Honeywell and competitive controls without replacing existing spark cable. For a full list of all the models this replaces, please check the charts that are uploaded into the gallery to check if your model is listed, thanks! INSTALLATION TIPSLED Error Codes:OFF: No call for heat, TH-W does not have 24VAC presentFast Flash: Power up - internal checkHeart beat (1/2 sec bright, 1/2 dim cycles): Normal start up, ignition sequence started4 secs on then x flashes: Device in run mode. "x" = flame current2 flashes: 5 minute retry delay3 flashes: Flame failed during run4 flashes: Flame sensed out of sequence5 flashes: Damper error. Make sure 24V terminal is not connected if P1 plug is not used6 flashes: Control internal error7 flashes: Flame rod shorted to ground8 flashes: Low secondary voltage supply. Check transformer and AC lineIMPORTANTTH-W should be connected to 24VAC from the thermostat24V GND should be connected to the unswitched leg of 24VAC transformer24V should NOT be connected if P1 vent damper is not usedDISCLAIMER: Failure to follow instructions carefully can result in injury or cause damage to the product. Check the ratings given in the instructions to make sure the S8610U module is suitable for your application. The installer must be a trained, experienced service technician. After installation is complete, check out operation as provided in these instructions. Babybluetriton is not responsible for how the product is installed.